Storage systems TESVOLT — these are professional and flexible modular solutions for any situation. Various configurations are available through 4.8 kW·h for indoor and outdoor installation. TESVOLT batteries allow operation in both stand-alone and grid-connected power supply systems.
Storage systems TESVOLT provide uninterrupted power supplies for private homes, hospitals and data centers, smooth consumption peaks, allow the creation of an autonomous network, or increased own solar power consumption.
TESVOLT uses extremely safe and environmentally friendly nickel-manganese-cobalt-oxide based technology, enclosed in 14 prismatic cells with such high-quality as those that have been employed in electric cars so far.
The unique Active Battery Optimizer (ABO) — battery balance managment provides detecting differences in battery systems and correct them on a continuous basis. This process significantly increases the lifespan of individual cells up to 30 years and 8,000 cycles. Charging and discharging current on long-term basis is 1C and even at 4C for short periods (max. 20 seconds).
Controlled distribution of energy across individual cells and in every module
Cells Samsung SDI do not contain environmentally harmful heavy metals and can be completely recycled at the end of their service life. TESVOLT offers a take-back scheme for their batteries at no additional cost for customers.
Example of instalation of TESVOLT TS48V Lithium Storage systems
48-voltage systems TESVOLT are optimized for work with battery inverters SMA Sunny Island and could be installed in three different size racks:
|System TS 25 (1300×600×600 mm)|
|Number of batteries||3||4||5|
|Price in BGN||27 925||34 535||41 150|
|System TS 40 (1900×600×600 mm)|
|Number of batteries||6||7||8|
|Price in BGN||48 715||55 330||61 940|
|System TS 50 (2300×600×600 mm)|
|Number of batteries||9||10|
|Price in BGN||68 960||75 575|
Prices include delivery to Bulgaria and VAT 20%
Systems include: rack, batery modules, active power unit (APU), 8-port ethernet switch, connection kitBuy or ask
All battery modules are connected in parallel between each other providing low voltage for any capacity of the storage. This solution increases flexibility and safety of the whole system. According of tasks there are single (one inverter) or three phase sollutions (with three inverters):
Storage system 76.8 kW·h for three-phase grid
Single active power unit (APU) provides control up to 16 battery modules, forming a cluster. A multicluster storage system is formed by needed number of clusters
High voltage systems TESVOLT are optimized for work with three phase battery inverters SMA Tripower Storage 60 and they are installed in two racks with dimensions 1900×1200×600 mm:
|Double rack system (1900×1200×600 mm)|
|Number of batteries||14||16|
All battery modules are connected in series wich increase the voltage of the whole group up to 930 volts with remaining the value of current and thus the same cable diameter is used. Bigger systems are build by connecting few of those equipments.
Outdoor version significantly increases the field of application of high voltage storage systems. A strong heat-insulated housing with a ventilation system allows it to operate in a temperature range from −33 up to 55 °C.
External systems are applicable to optimize diesel generation, increase peak power, increase solar power consumption or create charging infrastructure.
Application of storage system TESVOLT HV 70 Outdoor as a car charger station
Each rack includes 14 or 16 battery modulesBuy or ask
A container energy storage system is a convenient and practical solution for megawatt projects. TPS is optimized for use with SMA Sunny Central Storage System inverters of varying power. Using 3 sizes for containers and 3 sizes of battery cabinets, it is possible to obtain multiple combinations for capacity and power in large-scale aplications.
|TPS Storage System|
|Container size, ft||20||40||45|
|Number of the storage systems||до 12||до 24||до 28|
|Max energy, kW·h||864||1 728||2 016|
Choose a convenient way to contact or fill in this form: