Many agricultural facilities are not connected to power grids. Therefore, farmers use diesel generators to provide energy for the equipment they ...Electricity for dogs
Near the town of Ignatievo, Varna is situated a small kennel for breeding German shepherds. The kennel itself, isn’t connected to the ...Autonomous power plant for a country house
«I need complete independence from energy suppliers» — said the owner of the house under construction. We at NENCOM ...First time in Bulgaria: BYD Battery Box Premium LVL
The Chinese giant BYD, known for its electric buses, cars and energy storage systems, has launched a new series of household batteries BYD Battery ...Electricity for sheep
In December 2019, we were contacted by farmers from the village of Zlatna niva, Shoumen district. Modern agriculture is impossible ...Spatial development act
«Закон за устройство на територията» (ЗУТ) regulates public relations, associated with spatial planning, investment design and ...Solar power station in Varna #2
In August 2019, we built the second hybrid solar power plant in Varna. Customer purpose — reduce electricity bills and stock ...
Our company has recieved a request for a diagnosis of a hot water supply system in a private house. The old solar collector stopped heating the water normally, and the owner was increasingly forced to use the gas boiler, which was connected to the water heater by a second heat exchanger.
After the check, we came to the conclusion that the gaseous coolant had partially evaporated from the pipes of the vacuum manifold. We tried to find new pipes, but the Chinese manufacturer no longer exist and the company that installed the entire system 9 years ago, changed its profile.
The old solar collector after dismantling
As we were unable to find spare parts and all other components of the system were working properly, we propose to replace the solar collector. After discussing different options with the client, we installed the new model of VIESSMANN with overheating protection — the flat-panel solar collector Vitosol FM, the absorber of which automaticaly reduces the absorption coefficient of the solar energy depending on the heating of the heat carrier.
We have also pointed out to the client that the protective coating of the copper pipe insulation is in poor condition due to the external environment. As the insulation itself is in good condition, it was decided to replace only the protective tape.
Nothing else needed to be done: the pump and electronics worked fine. We were especially pleased with the 150 liters water heater ELDOM, which has been installed under the roof for 10 years without complaint.
Solar thermal collectors unlike solar PV-panels do not produce electricity. They heat up water or antifreeze. Modern models are able to heat ...
Choose a convenient way to contact or fill in this form: