Today we received equipment from China, Austria and the Netherlands, including the latest solar charge controller Victron Energy RS 450 | ...First time in Bulgaria: BYD Battery Box Premium LVS
Recently, we talked about the new generation of lithium iron phosphate batteries by BYD with prefix «Premium». In March ...Electricity for cows
Many agricultural facilities are not connected to power grids. Therefore, farmers use diesel generators to provide energy for the equipment they ...Autonomous power plant for a farm building
«I need complete independence from energy suppliers» — said the owner of the building under construction. We at NENCOM ...First time in Bulgaria: BYD Battery Box Premium LVL
The Chinese giant BYD, known for its electric buses, cars and storage systems for electric energy, has launched a new series of household batteries ...Electricity for sheep
In December 2019, we were contacted by farmers from the village of Zlatna niva, Shoumen district. Modern agriculture is impossible ...Spatial development act
«Закон за устройство на територията» (ЗУТ) regulates public relations, associated with spatial planning, investment design and ...
Near the town of Ignatievo, Varna region, a small kennel for breeding German shepherds is located. The facility itself isn’t connected to the electricity grid, so the owner of the kennel asked us to create an autonomous solar power plant. Until now he has been using a gasoline generator.
It was necessary to provide energy for a water pump, refrigerator, freezer, TV, router and lighting. We discussed the budget and configuration of the system with the client, and started the work.
We installed on the roof of the aviary four Risen modules, 330 watts each. The total peak power of the solar panels is 1.32 kWp.
To work during the night time, in the system we added two 12 volt Victron Energy AGM Deep Cycle batteries, 220 A·h each. We connected them in series to obtain a nominal voltage of 24 V. The useful energy reserve at a permissible unloading depth of 50 % is 2.64 kW·h.
The batteries are charged using a solar controller Victron Energy MPPT 100 | 50, with power of 1.4 kW. The input parameters of this controller allow the addition of two more 330 watts solar modules to increase the generation in dark weather.
To convert direct current from the controller and batteries to alternating current, we installed Victron Energy inverter Phoenix 24 | 1200, with power of 1.2 kV·A or 1 kW. The inverter has a peak power of 2.2 kW, therefore it can successfully handle the inrush current of the water pump and compressors in the refrigeration equipment.
Block diagram of the power plant
As the budget was limited, we did not install the remote monitoring system module, but it may be added in the future.
According to the client, the system works perfectly, the dogs are satisfied, a slight energy deficit occurs only on dark winter days. This disadvantage can be eliminated by adding two solar modules.
The price of this solar power plant in June 2020 was 5 500 BGN (2 800 €) with delivery, installation and VAT.
In December 2019, we were contacted by farmers from the village of Zlatna niva, Shoumen district. Modern agriculture is impossible ...
Many agricultural facilities are not connected to power grids. Therefore, farmers use diesel generators to provide energy for the equipment they ...
Choose a convenient way to contact or fill in this form: